Download original image
Test Window electric output and daily energy monitoring results. (a) Instantaneous PV voltage variations (at MPPT, as monitored in real time by Victron 75/10 Charge Controller during morning hours); (b) an example I–V curve of a solar window with a low-quality interlayer measured with PROVA 200A PV Module Analyzer at close to optimum window orientation, featuring a distorted I–V curve shape with side-peaks in the power-voltage curve; the output electric parameters also illustrate the significant reduction in the fill factor (FF) from its expected value of near 0.76; (c) daily energy output of Test Window measured by Victron 75/10, monitoring done for 21 days; data are plotted against the measured (per-window average) energy outputs of other solar windows installed in nearby wall arrays, and the wall average measured from 30 windows (arrays J, F, and C); (d) measured intra-day electric power output traces.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.